Vesta mayor fabricante alemán de Aerogeneradores, identifica falla que provocó fuego en aerogenerador de 3 MW:
The fire started in the harmonic filter cabinet due to a loose connection in the electrical system, which created an arc flash. Vestas says the issue is being addressed by using a different type of washer on the the electrical connections in the wind turbine's harmonic filter cabinet. V112 customers have been informed, and Vestas is already in the process of replacing washers at the same time as performing other planned upgrades and maintenance of the wind turbines. The burnt nacelle has already been replaced, and is scheduled to be re-commissioned this week. Vestas still is awaiting the reports from two external experts who worked side-by-side with Vestas investigators. The these reports are expected within a few weeks, and Vestas says it is confident that this final conclusion will be confirmed.